The following horizontal clearances to other utilities from underground service lines and equipment, including padmount transformers, switching cubicles, guardrails, and ground grids, must be maintained:
- Secondary conductors
- 2.0 metres to all valves, hydrants, catch basins, manholes, vaults, sanitary and storm sewer lines, septic tanks, fields, and Minnesota mounds. The secondary cable cannot cross through septic fields and Minnesota mounds.
- 1.8 m to all water lines and cc valves.
- 1.0 m to all gas lines.